The importance of routine maintenance is clear to see in this photograph. A stalled motor caused an overload fault which was not cleared by the respective protection device. Subsequent investigation attributed complete failure of the motor and associated MCC cubicle to a failed motor overload device thus causing severe overheating and subsequent fire. The clients [...]
Failed ABB Sace Megamax back in the workshop after being replaced with a retrofit solution in the form of an ABB Emax 2 We also undertake circuit breaker maintenance, repair & overhaul both onsite and within our workshop facility in Norwich.
LS Engineering Services are pleased to announce the successful completion of another ‘intelligent’ switchboard for the UK Defence sector. This 440VAC 2000A switchboard has been manufactured at our site in Norwich in conjunction with Proeon Systems Following stringent in-house testing the switchboard has now been installed and tested at our clients facility in the north [...]
LS Engineering Services are pleased to announce the successful completion of an 'intelligent' switchboard for the UK Defence sector. This 440VAC 6300A switchboard has been manufactured at our site in Norwich in conjunction with Proeon Systems Following stringent in-house testing the switchboard has now been installed and tested at our clients facility in the north [...]
LS Engineering Services Ltd have recently undertaken work on the Apache Beryl Bravo platform as part of the installations Delta V control system upgrade. This work involved the installation of control components and associated wiring modifications to a large quantity of LV MCC and MV cubicles to enable the platform remote operation of various drives. [...]
LS Engineering Services Ltd have just completed the first of a number of contracts for AAF Ltd on behalf of National Grid. The work has involved in-house modification and overhaul of a number of LV starter cubicles, on-site installation, testing and Ex glanding and terminating.
LS Engineering Services have recently completed the retrofit installation and commissioning of 13 Teresaki ACB's on the North Cormorant Platform. LS Engineering Services initially carried out a detailed site survey of the exisiting Merlin Gerin ACB's and then worked closely with Teresaki to engineer a retrofit solution. The installation work included removing the exisiting ACB's [...]
LS Engineering Services Ltd site support team recently completed the overhaul of 3 MV Gas Compressor Motors for a major Onshore Oil and Gas plant in Southern England. These activities included detailed inspections and remedial work including the replacement of worn labyrinth seals.
LS Engineering Services have recently completed switchgear modification / upgrade work on the Brent Bravo Platform. The work undertaken included the on-site installation of new components, control circuit re-wiring and subsequent testing, these modified cubicles will form part of the platforms decommissioning infrastructure.
LS Engineering Services are pleased to announce that they have recently successfully completed phase one of a major ACB and MCC upgrade project for an Oil & Gas major in the Central North Sea. Phase 1 involved the retrofit installation and commissioning of 4 Teresaki ACB's (1600A, 2000A & 3200A) and 8 new MCC cubicles. [...]