The Brent Alpha platform was the first offshore installation we visited just a few days after the company formed back in 2007. Since then our technicians have visited many offshore installations both on the UKCS and abroad. Our oil and gas electrical engineering experience is extensive and we look forward to continuing our support both [...]
The importance of routine maintenance is clear to see in this photograph. A stalled motor caused an overload fault which was not cleared by the respective protection device. Subsequent investigation attributed complete failure of the motor and associated MCC cubicle to a failed motor overload device thus causing severe overheating and subsequent fire. The clients [...]
Failed ABB Sace Megamax back in the workshop after being replaced with a retrofit solution in the form of an ABB Emax 2 We also undertake circuit breaker maintenance, repair & overhaul both onsite and within our workshop facility in Norwich.
LS Engineering Services are pleased to announce the successful completion of another ‘intelligent’ switchboard for the UK Defence sector. This 440VAC 2000A switchboard has been manufactured at our site in Norwich in conjunction with Proeon Systems Following stringent in-house testing the switchboard has now been installed and tested at our clients facility in the north [...]
LS Engineering Services Ltd are pleased to announce that work is now well underway on another large LV switchboard for the Defence Sector. This switchboard will again incorporate ABB’s ‘smart’ range of switchgear products including the ABB Emax and ABB Tmax circuit breakers. In order to give our client not only the best in switchgear design and manufacture [...]
Here at LS Engineering Services Ltd we hold an extensive range of spare parts for the Laurence Scott ranges of switchgear including CentaurTM and Slendaur TM Where spares are obsolete we have the expertise and knowledge to recommend and advise on suitable retrofit replacements. View our range of spares
LS Engineering Services are pleased to announce the successful completion of an 'intelligent' switchboard for the UK Defence sector. This 440VAC 6300A switchboard has been manufactured at our site in Norwich in conjunction with Proeon Systems Following stringent in-house testing the switchboard has now been installed and tested at our clients facility in the north [...]
LS Engineering Services Ltd have recently undertaken work on the Apache Beryl Bravo platform as part of the installations Delta V control system upgrade. This work involved the installation of control components and associated wiring modifications to a large quantity of LV MCC and MV cubicles to enable the platform remote operation of various drives. [...]
LS Engineering Services Ltd have just completed the first of a number of contracts for AAF Ltd on behalf of National Grid. The work has involved in-house modification and overhaul of a number of LV starter cubicles, on-site installation, testing and Ex glanding and terminating.
LS Engineering Services have recently completed the retrofit installation and commissioning of 13 Teresaki ACB's on the North Cormorant Platform. LS Engineering Services initially carried out a detailed site survey of the exisiting Merlin Gerin ACB's and then worked closely with Teresaki to engineer a retrofit solution. The installation work included removing the exisiting ACB's [...]